# Diagnostic Features of the Technical Condition of Turbogenerators Stator Winding of Ukrainian Nuclear Power Plants

О. V. Vygovskyi

Institute for Safety of Problems of Nuclear Power Plants, NAS of Ukraine,
12, Lysogirska st. Kyiv, 03028, Ukraine

DOI: doi.org/10.31717/2311-8253.20.1.3

### Abstract

Given statistics of Ukrainian NPP turbogenerators failures for 2011-2017 was shown that machines with a capacity of 1,000 MW have insufficient reliability. This is a significant factor reducing the safety, reliability and efficiency of the power units operation in general. New three-dimensional mathematical model for calculating the temperature field of turbogenerator stator winding that allows to determine diagnostic features of the technical condition of mentioned winding was developed. Discrepancy of experimental and calculated data on non-stationary (for starting) and stationary heating of stator winding bars of turbogenerator type TVV-1000-2U3 with a capacity of 1,000 MW is less than 5 %, that confirms the accuracy of developed techniques, algorithms and mathematical apparatus. With a help of developed mathematical model the theoretical studies of three-dimensional temperature field of stator winding bars for starting the turbogenerators types TVV-1000-2U3 and TVV-1000-4U3 with such defects as stopple of a hollow conductor and increased current in a hollow conductor of stator winding bar are carried out. Studies have shown when stopple of hollow conductor occurs the start time regularization and time constant of the regular mode are increasing significantly for both a copper hollow conductor and resistance thermometer, while the initial derivatives remain unchanged. For high current in a conductor, the start time regularization and time constant of the regular mode remain unchanged and the initial derivatives increase significantly. Thus, according to the results of information processing from devices of staff heat control, it is possible to diagnose these defects, in particular, coil fault, reliably and effectively. At the NPP tests can be conducted at planned startups, load changes or unload of power units.

Keywords: turbogenerator, stator winding, mathematical model, damages, diagnostic features.

### References

1. Vygovskiy A. V. (2016). [The basic problems of development of nuclear energy in Ukraine and ways of their decision]. Problemy bezpeky atomnykh electrostantsiy i Chor-nobylya [Problems of Nuclear Power Plants Safety and of Chornobyl], vol. 27, pp. 5-12. (in Ukr.)

2. Ministry of Fuel and Energy of Ukraine. Basic and Renewed energy strategy of Ukraine till 2035. Available at: http://mpe.kmu.gov.ua/minugol/control/uk/doccatalog/ list?currDir=50358. (in Ukr.)

3. Kensytskyi O. G., Fedorenko G. M. (2016). [Reliability of generating equipment and prospects of Nuclear power development in Ukraine]. Problemy bezpeky atomnykh electrostantsiy i Chornobylya [Problems of Nuclear Power Plants Safety and of Chornobyl], vol. 26, pp. 69-74. (in Ukr.)

4. Ministry of Fuel and Energy of Ukraine. NEK “Ukrenergo”. Official web-site. Available at: http://www.ukrenergo.ener-gy.gov.ua/ukrenergo (in Ukr.)

5. Government service of statistics. Official web-site. Available at: http://www.ukrstat.gov.ua. (in Ukr.)

6. Energoatom Ukraine. Official web-site. Available at: http://www.energoatom.kiev.ua. (in Ukr.)

7. Kyrylenko O. V., Kensytskyi O. G., Fedorenko G. M. (2013). Complex analysis of emergency situations of generating equipment of power station. Proceedings of the III International scientific and practical conference “Improving the safety and efficiency of nuclear energy” (Odesa, November 24-28, 2012). Odesa: NPC “Energoatom” SPC, pp. 203-215. (in Ukr.)

8. Polyakov V. I. (2001). Diagnostics of the technical condition of water cooling channels and the fastening of the core of the windings of powerful turbogenerators to extend their service life. Elektricheskie stantsii [Power stations], vol. 10, pp. 34-39. (in Russ.)

Full Text (PDF)

Published
2020-02-29

If the article is accepted for publication in the journal «Industrial Heat Engineering» the author must sign an agreement on transfer of copyright. The agreement is sent to the postal (original) or e-mail address (scanned copy) of the journal editions.

Authors retain copyright and grant the journal right of first publication with the work simultaneously licensed under a  Creative Commons Attribution License International CC-BY that allows others to share the work with an acknowledgement of the work’s authorship and initial publication in this journal.

Insert math as
$${}$$